1/2" x 1000ft PEX-AL-PEX Tubing
Mfr Part#: APX1210
1000ft roll of 1/2" PEX-AL-PEX Tubing for use in radiant heating applications.
Meets/exceeds ASTM F1281, CSA B137.10 standards.
Also certified for use in domestic water applications. UPC listed by IAPMO.
Pressure rated at: 80psi @ 200F, 160psi @ 140F, 200psi @ 73F.
Packing: Box. Weight: 74.0 lbs. Dimensions: 30" x 30" x 12".
1/2" PEX-AL-PEX Tubing is commonly used for radiant heating applications projects such as concrete slabs (wire mesh or rebar reinforced), thin slabs (non-reinforced), below the subfloor heating (staple-up), sandwich type installations (between subfloor and finished floor) and many others.
Typical loop length for 1/2" PEX-AL-PEX varies from 250ft to 350ft, depending of the application, supply temperatures, flow rates, etc. 300ft is considered standard for typical concrete slab install.
PEX-AL-PEX tubing can be installed using compression style PEX Fittings of Press type system (fittings, sleeves and tools).
Uponor (MultiCor/MLC): D1220500
Watts (RadiantPEX-AL): RL0508-1000-OR
Zurn (Alumicor): Q3PAP1000X
And same size Viega FostaPEX tubing in various coil lengths.
What is the OD of 1/2" Pex-Al-Pex?
Read 1 answer
OD of 1/2" PEX-AL-PEX is 0.63".
Answered on 4/19/2016 by PexUniverse Customer Service
Is there a spec sheet for Everhot Pex-Al-Pex that would list bend radius and expansion coefficients for their 1/2" PAP?- are the inner/outer layers of the PAP made with Type B PEX?- Everhot has an 'installation manual' for their Barrier / Non-Barrier PEX - is there a similar manual for the PAP type PEX?
Read 1 answer
Expansion coefficient for all PAP sizes is 0.3" per 100ft for every 10F change. Manufacturer recommended minimum bending radius of PEX-AL-PEX is 5 times the outside diameter. For 1/2" pipe it would be around 6.5".
Answered on 12/14/2015 by PexUniverse Customer Service